Cambridgeport is currently manufacturing the highest quality carrier & bryant economizers available. Now partnered with the belimo zip economizer module and belimo actuator. Setup of an economizer has never been so simple and reliable.
The most reliable, energy efficient air-side economizer in the industry. easily set up by just entering your zip code and minimum outside air percentage.
Now with Belimo shaft-mounted actuator
This reliable and code compliant actuator is equipped with a feedback loop which allows your economizer control to see the position of your damper in real time. This feature allows the economizer module to see problems as they are happening and initiate alarms as necessary to ensure you are always operating at maximum efficiency.
Cambridgeport economizers are convertible and can be installed in both the downshot and side return orientations.
Which economizer is right for me?
This economizer is wired for new Carrier/Bryant rooftop units. This wiring will work with most units built after 2008. Unit must have ctb board (see pic) this economizer can be re-wired for older units. (20-30 min process. See manual)
This economizer is wired for most Carrier/Bryant units built before 2008. These are units with no CTB board. Zip module is pre-mounted to top of economizer.
Central Terminal Board (CTB)
Typically found in units manufactured after 2008. If present, use standard economizer. Do not confuse with ignition board.
Ultra low leak economizers
In many areas ultra low leak economizers are now required by code. Cambridgeport’s u.l.l. economizers meet and exceed the latest ASHRAE and IECC building codes. These economizers have been tested and labeled by an approved 3rd party testing facility in accordance with AMCA 500-d. Dampers tested and labeled are as follows:
Supply & return air dampers
Leakage rates less than 4 CFM/ft²
Barometric relief dampers
Leakage rates less than 20 CFM/ft²